Question about Cutler Hammer 100 Amp Main Breaker Resident Load Center
I don't want to go way over board but still be safe.
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The most likely causes in their order of probability are: 1) water somewhere in the circuit causing the hot wire to ground; 2) a legitimate trip caused by a defect in a device plugged into the circuit; and 3) a defective GFCI breaker. In the first case, wait until it has been dry for about a week and see if it trips. In the second case, make sure there is nothing plugged into the circuit and try resetting. In the third case go ahead and put the regular breaker in, then put a GFCI outlet into the first box downstream from the breaker. If installed according to the directions, that outlet should protect all of the outlets downstream.
Posted on Feb 27, 2009
You can Google the catalog number for that breaker. You can also try to call local electrical contractors as one can usually find at least one contractor who has saved every old part that they have removed over the years. Also try ebay.
Unfortunately, even if you do find the correct breaker it will probably be very expensive :-(
Posted on Dec 10, 2009
I answer questions for free
I specialize and timers and electrical devices
Looking up your breaker at Eaton, I found the chart that shows below:
Other than the chart, I do not know the specifics of your breaker.
You can add a comment, and I can help you with your wiring project.
Another good source of information about specifics are your local Graybar electric supply house, or any local supplier that specializes in electric wiring.
Having a local electrician stop by and look at your project for a fee might be a good investment long term because that person knows local codes and restrictions.
The #1 Data Table from manual shows CU/AL which is copper/aluminum
2/0 wire fits CH145 CH245 CH150S breakers
See the manual
Posted on Nov 02, 2010
Tips for a great answer:
Feb 21, 2015 | Square Electrical Supplies
Sep 26, 2012 | Square D Qo 200 Amp 40 Circuit Indoor...
Jan 04, 2012 | Siemens 100 Amp Main Breaker Renovation...
Jul 20, 2011 | Siemens 100 Amp Main Breaker Renovation...
Jun 01, 2011 | Square D Qo 200 Amp 40 Circuit Indoor...
Jan 27, 2011 | Siemens 200 Amp Main Breaker 30 Spaces 40...
Dec 04, 2010 | Pacific Industrial 100 Amp Federal Pacific...
Oct 03, 2010 | Siemens 100 Amp Main Breaker Renovation...
Sep 21, 2010 | Cutler Hammer 100 Amp Main Breaker...
Jun 19, 2010 | Cutler Hammer Cutler-Hammer...
Mar 24, 2013 | Cutler Hammer 100 Amp Main Breaker...
181 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: