Question about KDS Valiant 6380iPTD-01 Notebook
I take it this is a Vaillant EcoTec boiler? If your having to pressurise to 2.0 before the F75 goes, there's a strong probability there's a problem with the water pressure sensor. These can sometimes just have dirt/sludge in them, and can be cleaned, however a lot of the time they just need to be replaced. F75 can also mean there's a circulation problem through the boiler, and you will get the same fault code. If you have the old rubber hoses on the flow and return pipes, these can be prone to blocking/restricting and Vaillant have actually modified this part whereby by the pipes are solid copper.
Posted on Oct 16, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 02, 2017 | Water Heaters
Nov 12, 2013 | Heating & Cooling
Oct 27, 2012 | Universal 900MM Super Thermocouple Baxi...
Sep 14, 2010 | Heating & Cooling
Jan 26, 2010 | Heating & Cooling
Jun 15, 2009 | Water Heaters
Apr 17, 2009 | Water Heaters
330 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: