Question about Heating & Cooling
Need wiring diagram for heat pump Model: CH5024UKB3
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If no blowing air is coming out to your ac or evaporator fin,your blowing fan is not working.There are several factor to check qualified electrician or ac techician should do this.If you have knowledge on electricity and motor control,beside you should have clamp ammeter to use in trouble shooting of ac electrical circuit.Unplug your ac If there is an opening of blower fan of your ac mostly the top cover open this one locate the wire connection of blowing fan take the color and size.Open the terminal box below the control panel of ac and locate the wire of blowing fan.Check how many leads make sure to make sketch where it was connected from low,medium, and high there is coded color on it,discannect from the terminal, using clamp ammeter set to ohms probe setting R10 check continuinity of winding motor start at common lines(mostly balck color) of one test rod and the other to starting line(mostly red color)take and read the resistance if has a higher resistance your motor is burn out, also with the running line w/c has multple line for speed.If resistance complied to your motor rating or good,If not or burn out replace fun motor.Check your capacitor,doing this set your ohmeter to a higher resistance,connect one red test rod (+) one terminal of capacitor and one black test rod on (-)the other terminal the pointer will deflect steady to higher resistance then reverse the connection of the test rod,the pointer deflect again to higest resistance it will go slow backward setting to zero if you got this result your capacitor is good.But if it does not go set back to zero your capacitor is short.Replaced capaciter.
Posted on Mar 13, 2009
Unfortunately, the wiring diagrams for heat pumps are not so easy to come up with. The outdoor unit will have its own diagram, but may not include the indoor air handler and will probably not include the thermostat. That said, the orange wire is commonly run from the thermostat to the reversing valve in the outdoor unit. This wire is usually not connected to the indoor airhandler. The orange wire is usually used in a unit that has the reversing valve energized in cool. Ruud, however has its reversing valve energized in heat. Probably not useful but maybe helpful
Posted on Mar 26, 2009
look on the indoor unit and see what they do you hav common from trans former yellow for compressor white for elect heat then reversing valve usually orange green for fan on the out door unit board you can tell what is common and what is for heat
Posted on May 09, 2009
Tips for a great answer:
Dec 30, 2016 | Heating & Cooling
Jan 21, 2016 | Motorcycles
Aug 06, 2014 | Heating & Cooling
Nov 21, 2013 | Universal ICP Heil Tempstar 10 12 KW Heat...
Oct 11, 2013 | Heating & Cooling
Aug 31, 2011 | Heating & Cooling
Oct 21, 2009 | Heating & Cooling
Mar 10, 2009 | Heating & Cooling
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: