Question about Air Conditioners
Need someone who knows how to troubleshoot older oil furnaces.
the oil filter and spray nozzle have been replaced, there is no air in the line and the tank is full but when you hit the reset button it runs for about 30 seconds and then shuts off, its like it won't catch (take off)
very frustrating during winter time, any ideas?
You have a flame rectifier that has to sense the flame. Try cleaning it just looks like a small round device off to the side. They get covered with soot and can't prove the flame is on. Let me know how it goes. ken
Posted on Jan 12, 2009
Tips for a great answer:
Oct 02, 2014 | Air Conditioners
Aug 21, 2014 | Air Conditioners
Dec 05, 2012 | Coleman Intertherm Nordyne Miller Furnace...
Oct 08, 2012 | Coleman Mobile Modular Home Electric...
Nov 03, 2011 | Intertherm P3RA-048K Air Conditioner
Feb 16, 2011 | Air Conditioners
Oct 06, 2010 | Air Conditioners
Dec 05, 2009 | Air Conditioners
139 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: