Question about Heating & Cooling
Need someone who knows how to troubleshoot older oil furnaces.
the oil filter and spray nozzle have been replaced, there is no air in the line and the tank is full but when you hit the reset button it runs for about 30 seconds and then shuts off, its like it won't catch (take off)
very frustrating during winter time, any ideas?
You have a flame rectifier that has to sense the flame. Try cleaning it just looks like a small round device off to the side. They get covered with soot and can't prove the flame is on. Let me know how it goes. ken
Posted on Jan 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 27, 2016 | Heating & Cooling
Mar 02, 2015 | Heating & Cooling
Oct 02, 2014 | Heating & Cooling
Oct 08, 2012 | Coleman Mobile Modular Home Electric...
Dec 20, 2010 | Heating & Cooling
Jan 27, 2009 | Heating & Cooling
Jan 20, 2009 | Goodman GMS90703BXA Heater
Nov 21, 2008 | SySTOR Systems (400S52) Burner
144 people viewed this question
Usually answered in minutes!