Question about Aprilaire 600 Humidifier
Water to the unit but not past the control valve. I cleaned out hard water sediment but the solinoid doesn't appear to open the valve
Make shure that the the filter in the bottom of the valve is clean. Turn water off use a 1/2 & 7/16 wrench to take apart the bottom connection on valve use a small screwdriver and push the small screen out and clean then put it back together.Use the same wrenches and take apart the top of valve clean inside valve and clean small orfice in plastic water line put back together. Make shure 24volts is gettin to valve you should her a click when furnace is running or fan. It may take a couple times to clean. Hope this helps
Posted on Jan 14, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 31, 2011 | Aprilaire 550 Humidifier
Feb 27, 2011 | Aprilaire 550 Humidifier
Feb 14, 2011 | Aprilaire 550 Humidifier
Dec 15, 2010 | Aprilaire 550 Humidifier
Mar 10, 2010 | Aprilaire Humidifiers
Dec 03, 2009 | Aprilaire 600 Humidifier
Nov 07, 2009 | Aprilaire 700 Humidifier
Oct 30, 2009 | Aprilaire 600 Humidifier
Dec 13, 2008 | Aprilaire 600 Humidifier
Nov 11, 2007 | Aprilaire 550 Humidifier
May 22, 2017 | Aprilaire 600 Humidifier
166 people viewed this question
Usually answered in minutes!