Question about Electrical Supplies
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Generac Guardian 15kW Generator
That sounds just about right, if the relay contacts get welded together it sometimes takes out the driver on the printed circuit board. As you found out, 12vdc from 23 to 194 makes the transfer switch move to the Generator position, relay not energized makes the ATS move to the Normal position.
You can make a nice test function by installing a 10 amp contact switch in series with either the N1 or N2 terminals. When the switch is open the generator thinks the Normal power has failed.
Posted on Jan 26, 2009
by ats I assume that you mean an (automatic transfer switch) this is a very non forgiving installation please (no disrespect intended) get a professional to do this for you. you are mixing generator supplied voltage with residential hydro depending on your situation you could end up back feeding the grid and put your self and / or your neighbours in harms way no b/s my friend I have seen it "not pretty"
Posted on Oct 23, 2009
It is always good to install a large enough wire where the maximum load can be drawn plus a little extra for safety. 7 gauge wire will do, if it was mine I would use 6 gauge wire. If the length is over 20 feet but not longer than 80 feet go to the next larger size wire.
Posted on Dec 18, 2010
Tips for a great answer:
Mar 01, 2015 | Generac Electrical Supplies
Oct 16, 2014 | Generac 10kw Whole House Generator with...
Nov 08, 2013 | Generac Electrical Supplies
Feb 12, 2013 | Kohler Generator 20kw 20res W/ 200 Amp...
Feb 21, 2012 | Winco 100-Amp Automatic Transfer Switch -...
Jul 09, 2011 | Briggs & Stratton Briggs Stratton 7 kW...
Jun 09, 2011 | Kohler Electrical Supplies
Oct 18, 2009 | Electrical Supplies
Apr 07, 2009 | Winco 200-Amp Automatic Transfer Switch -...
Jan 20, 2009 | Generac Guardian 100 Amp Transfer Switch...
33 people viewed this question
Usually answered in minutes!