Question about Fujitsu Heating & Cooling
Fujitsu aircon leaking on left side inside room
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Make sure the unit is level, this is very important. Check for blocked drain tube, which runs from the bottom of the drain pan under the cold coil to the outside. Clear tube with a piece of coathanger wire, be gentle.
Posted on Jul 15, 2007
Go to http://www.fujitsugeneral.co.nz/scripts/get-manual.pl?manual_id=36 to get the manual. Any questions please ask. Please rate me so I know if I helped.
Posted on Dec 30, 2008
Either the drain line is clogged, or there is a hole in the pan.
Get a powerfull wet/dry shop vacume.
Attatch it to the end of the drain pipe and seal it tight and pull out any dirt, mold crud blockages.
Take the panel off so you can access the drain pan under the evap coil. Clean that out as well with the vac.
Once its nice and clean, poor a gallon or so of water into the pan bein g carefull to not pour to fast.
Make sure that the line is drainign well and look for any spots where there may be a crack, hole etc in the drain pan where water may leak out
Posted on Jan 01, 2009
1. Do not set the aircon too low temperature in overcast weather, this will cause ice ups and water dripping. Optimal comfort zone temperature is 24c.
2. You need to open the grill cover on the front of the aircon which unclips either end left and right with a finger pressure. You will find two filters which can slide out and should be cleaned. First tap them together to remove dust, then you can wash them with mild soap and cold water.
3. There is the third possibility that an insect has made a nest in the drainpipe. You should look on the outside of the building and locate a plastic drainpipe. You can either blow into this pipe with your mouth or get a blower. This will unblock any restriction in the drainpipe.
Goodluck and ratemeplease.
Posted on Mar 19, 2009
Tips for a great answer:
Jan 01, 2010 | 2007 Ford F
Jun 28, 2009 | Fujitsu Heating & Cooling
Jun 08, 2009 | Panasonic Room Air Conditioner CWXC104HU
May 23, 2009 | LG Heating & Cooling
Mar 19, 2009 | LG LSC121PMA Split System Air Conditioner
Feb 21, 2009 | 2006 Ford Focus
Jan 01, 2009 | Fujitsu 24R1 Air Conditioner
Dec 30, 2008 | Fujitsu 24C1 Air Conditioner
Feb 13, 2008 | Fujitsu 36CS Air Conditioner
87 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: