Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It's always possible that the limit "dial" switch is sticking leading you to believe that it's only at 150º.
How old is the furnace and when was it last cleaned.
Posted on Dec 12, 2007
If you know where the high limit switch is you can always cut the two wires and wire them together causing the limit to close. But what you have to watch out for is why the high limit is not closing. That means in your return air either you have a dirty return air duct, dirty filter, or you don't have all your registors open to allow the heat to escape the heat exchanger. Just watch over riding the system. The high limit switch should either be on or behind the blower, in the middle of the system right under the heat exchanger. any other questions about hvac just ask.
Posted on Jan 17, 2009
If the unit is around 6 years old then it could be the combustion air motor. If the unit is older then you need to inspect the heat exchanger for signs of cracks. Take the top off the unit to inspect. Check to see if the metal around the reset is hot and if it is then the switch is doing it's job. If the heat chamber is cracked then turn the gas off, because your home will have CO. This can kill you.
Posted on Jan 05, 2010
SOURCE: I have a rheem gas
Depending on the age of your furnace the limit swithes are part of the control board and are not individually serviced. You will need to replace control board. On the older units that used a seperate fan and limit the only thing you could do was change temperature settings. Hope this helps. Thanks
Posted on Nov 19, 2010
Tips for a great answer:
Nov 15, 2015 | LG Dle2301r Front Load Dryer dle2301r
Jun 23, 2015 | Heating & Cooling
Jun 24, 2014 | Rheem Pool & Spa
Mar 18, 2014 | Heating & Cooling
Apr 18, 2017 | Heating & Cooling
Nov 28, 2011 | Heating & Cooling
May 22, 2011 | Dryers
Feb 06, 2011 | Honeywell Heating & Cooling
Oct 07, 2010 | Whirlpool LTE6234D Top Load Stacked...
Sep 29, 2009 | Heating & Cooling
34 people viewed this question
Usually answered in minutes!