Question about Hunter Dryers
Have a ceiling fan with light that has a black wire with a white tracer on it. Unsure how to wire it. Am trying to have a switch for the fan and one for the light
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
is the fan working correctly, if it is not it could be a bad armature or field
Posted on Jan 20, 2008
SOURCE: wiring connection ceiling fan
copper to green , white to white , seperate the black and the black with th white tracer you wired together connect the black to the black and the black with white tracer to the red in ceiling , without looking this is my best advise ,good lk
Posted on Nov 27, 2008
SOURCE: Wiring a ceiling fan w/light
To add to red54's comments:
This is what I believe you have:
- one source in the ceiling box (black & white)
- one donwline circuit in ceiling box going to another wall/ceiling box (black&white)
- on switch wire in ceiling box coming from your wall switch (black & white) -- this is the white wire which will be hot when the switch is truned on
Here's how it should be connected:
- all 3 blacks in ceiling box connected together -- no other wires in this bundle
- white wire (which is hot when switched) coming from switch connects to the black/blackwhite fan wires
- connect all reamining white wires together in bundle
- connect all ground wires together
It's that simple. Trick is figuring out, of the three cables in the ceiling box, which is source, which is downline, which is switch.
Maybe red54's procedure can help you figure that out.
Posted on May 11, 2009
SOURCE: Hunter fan wiring
sounds like one of your connections is loose. Im not sure if i completely understand your description of how you re-hoked up your fan. Please tell me how many wires your fan has and colors and how many wires you have on the sensor remote. (lots of times if you draw a wiring diagram on paper you can figure it out) Basically you should have power coming from ceiling to remote sensor. Then the remote sensor should throw the power to either the fan or the light, so there should be two seperate leads coming out of the remote sensor to control either the fan or the light independantly.
Posted on Oct 07, 2009
Black to black. from fan
Blue to Black and white. from fan
White to white. from fan
The input is from ceiling supply
the black wire from fan is for motor.
the black and white is for the light.
Posted on Jan 02, 2010
Tips for a great answer:
May 14, 2014 | Hunter 52" Ceiling Fan With Light And...
Apr 20, 2011 | Hunter (25417) Ceiling Fan
Jan 22, 2011 | Hunter 21617 Palermo Ceiling Fan
Jan 01, 2011 | Hunter Dryers
May 03, 2010 | Hunter 27187 Remote Control
Jan 02, 2010 | Hunter 52" Ceiling Fan With Light And...
Sep 20, 2009 | Hunter 52" Ceiling Fan With Light And...
Jun 13, 2009 | Hunter 52" Ceiling Fan With Light And...
Sep 27, 2008 | Hunter 23852 Classic Original Ceiling Fan
Mar 24, 2008 | Hunter 20531 Vista Brushed Nickel Ceiling...
254 people viewed this question
Usually answered in minutes!