Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a Braemar LCB450-G
There are several possibilities, the drain valve is opening and closing, this causes water to fill the base, the float valve will not achieve the desired level so the fan will not start. This could be the drain valve actuator is U/S or the PC board. Have you tried to turn the main power off at the switch board for 1/2 hour?
Most occasions the service person will swap out all the units as they purchase it as a package. It is not cheap to replace these units.
Posted on Nov 26, 2010
SOURCE: fault code 049f,this fault shows
f-049 Check power supply voltage to the outdoor unit is correct (1ph ?220 Vac ±10% or 3ph ?380 Vac ±10%). If OK check fuses, if fuses OK, replace outdoor main PCB
Posted on Dec 13, 2010
Tips for a great answer:
Jun 14, 2014 | Cfm Prem-I-Air PEVC797 Air Conditioner
Mar 27, 2012 | Heating & Cooling
Feb 09, 2011 | Mastercool 67680 Evaporative Cooler Air...
Jan 01, 2011 | Mastercool 67680 Evaporative Cooler Air...
Nov 22, 2010 | Heating & Cooling
Nov 07, 2010 | Honeywell Programmable Thermostat Heater
Apr 23, 2010 | Mastercool 67680 Evaporative Cooler Air...
Feb 07, 2010 | Mastercool 67471 Evaporative Cooler Air...
136 people viewed this question
Usually answered in minutes!