Question about Coleman Heating & Cooling
Wiring diagram to install tgerminal block example togo switch to turn system on where does the blk wire go on terminal block from switch
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If you haven't already tried Coleman customer support, try Google. You can find owner's manuals for all kinds of things. good luck, John
Posted on Nov 07, 2008
If I understand your post correctly....You state that you are hooking up a 240v heater and towards the end you speak of removing jumpers...W2 terminals..ect. It sounds to me your trying to us a 24v low voltage thermostat instead of a Line voltage thermostat.That's what I'd take a look at.
Posted on Jan 21, 2009
SOURCE: Dayton Heater M/N 3E227E
Hard to believe they sell a retrofit kit for a Gas furnace to a Customer....This is ahrd to advise you on with out seeing the schematic and if it is indeed intended for that furnace....the Spark mounting location is CRITICAL for safety so make sure that is correct above all.....OK The wire coming off the transformer and tied to the red wire going to the heat excghanger would most likely be a High Limit switch...cuts the gas off if the blower doesnt work etc or you would have a fire...so this switch must be in series with the transformer to cut power when the switch opens....the wire MV/PV coming from the "Electronic control box" needs to go to the New Gas Valve you should have which will have a termional marked MV/PV (Main valve/Pilot/valve) as your old one was for a standing pilot application and when you have electronic ignition you req a Gas valve for Intermittent pilot .....you should also have 2 more terminals on the valve MV and PV which will have seperate lines from the ignition control as well....basicvally there will be another wire coming from MV/PV going back to the transformer...make sure all wiring is correct and I would strongly advise you have a technician check your work before you attempt to use it....if wired incorrectly you could have a serious delayed ignition as its possible to power the main burner instead of the pilot if you wire it up wrong below is a typical spark wiring diagram....may not apply totally to your system but it will give you the general idea
Posted on Oct 31, 2009
Tips for a great answer:
Feb 20, 2018 | Coleman Heating & Cooling
Dec 22, 2015 | Coleman Heating & Cooling
Jan 15, 2015 | Coleman 7990-319p Evcon Gas Furnace...
Dec 11, 2013 | Heating & Cooling
Nov 26, 2013 | Coleman 7990-319p Evcon Gas Furnace...
Nov 29, 2012 | Heating & Cooling
May 15, 2011 | Coleman Heating & Cooling
Mar 11, 2011 | Coleman Heating & Cooling
May 20, 2018 | Coleman Heating & Cooling
103 people viewed this question
Usually answered in minutes!