Question about Ruud UAMB Air Conditioner
Unit works fine in heat mode, but starts clicking sounds like a relay kicking in and out. I can shut thermestat off and axu heat and obm continues to run. Runs in cooling mode without the clicking sound
Where can I buy emergency heat unit for RUUD UPNA 030J
Posted on Jan 05, 2010
I can tell you exaclty whats wrong . and it sounds like multipart problems. you have an old RUUD heat pump and its reversing vavle is stuck. without that valve opening it will contantly try to run in refrigerant mode to make heat. and here its 26 degrees, het pumps are only made to be effiient in over 34 degrees and that why your electric heaters in the blower section in an in a closit of unit
continously running up you eectric bill big time. cuses for the reversing valve to stick are sitting along time when it was low on refrigernt. or ust plain shut depending on its age. that cicking is the relay trying to open or close the reversing valve swict to make pressure again. any local guy an fix that one. theyre are kits called hard start kits that they hook up to them that shoot an extra zap of jiuse in it to try to free it up if its not totally lockd up being though that you still hear the relays pulling in and out thats good you may have just caught it in time.
now here is a quick test and possible cure but only if you what your doing turn both units off take off the top cover of the old rudd and get a small hammer not a sledgehammer and rap and tap all around the reversing valve. it will be a cylindrical tube black usually have sets of copper or brass tubings going in the 2 sides of this so dont hit itthat hard it gets dents it and is ruined. look for oil spots which uually means the refrigerant leaked out , and its seized up for good. they try spinning around the big out door fan door fan some. you may have to rock it back and forth Till it braks lose but dont put super human efort int it,
than put it all bak together making sure you connected wires back up right. go in and have you wife eithe watch it or you do it and switch the breker on and off about 8 times to trying to get the cnnectors switches to stay in and if your brave take a well insulated screw driver and hold them in for 2-4 miuntes to force it to work. if that doesnt do it call your local repairman and tell him you need a hard startkit only much safer, the cost about 40$ but you labor will be high if he is sent alone so may you can help im out and lessen your bill if the valve cant be made to work again. you may want start looking for prices with that model and serial number and d shut that electric heater off some one to replace it . I hope I helped you out some no charge ( I dont have my Pay Pal acct. set up yet ) good luck tom.
Posted on Jan 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 12, 2014 | Heating & Cooling
Aug 19, 2013 | Goodman Heating & Cooling
Oct 20, 2009 | Heating & Cooling
Sep 28, 2009 | Heating & Cooling
Jun 16, 2009 | Goodman CLJ36AR42 Air Conditioner
Jun 03, 2009 | Heating & Cooling
Apr 24, 2009 | Ruud Central System Air Conditioner
Apr 08, 2009 | Goodman Heating & Cooling
Apr 07, 2009 | Heating & Cooling
Apr 04, 2008 | Goodman CKL24AR24 Air Conditioner
Aug 08, 2013 | Ruud UAMB Air Conditioner
406 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: