Question about Honeywell Programmable Thermostat Heater
Your green wire from the tstat and the low voltage common should land on the relay coil. Your high voltage for the blower lands on normally open. Sounds like you are using your red (constant 24v) to energize your relay. Therefore your relay is constantly energized and your blower runs constantly. Let me know!!
Posted on Jul 01, 2017
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check to see if there is a short between the green wire and the red wire. Green is the fan control wire for AC. Sounds like some wires may be touching. How did the old t-stat get fried?
Posted on Jan 02, 2009
SOURCE: honeywell thermostat
I had the same problem and decided to take a chance and call honeywell customer support. I am shocked, they solved my problem! At least in my situation we found that the blue wire ran the compressor. Instead of hooking up to "blue" on the thermostat, we hooked it up to "white." It works wonderfully now.
Posted on Apr 25, 2009
red goes to RC and RH, White goes to W, Green goes to G and Blue goes to Y. iam assuming on the old tstat that Red whent to R White went to W Green went to G and Blue went to Y
Posted on Sep 20, 2009
Testimonial: "Thanks! Worked out great!"
SOURCE: Old wiring looks like this
If you have a heat pump, the thermostat that will operate it most generally will have an "O' terminal for the orange wire, this is the circuit that energizes the reversing valve on the heat pump, be sure that the stat says heat pump on the box. hope this helps
Posted on Nov 07, 2009
Tips for a great answer:
Feb 05, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Sep 12, 2013 | Goodman Heating & Cooling
Nov 15, 2012 | Goodman Manufacturing Goodman ARUF303016...
Jul 18, 2012 | Goodman Heating & Cooling
Jan 03, 2011 | Goodman CLQ36AR49 Air Conditioner
Jul 19, 2017 | Goodman Heating & Cooling
Jun 23, 2010 | Goodman CLJ30AR32 Air Conditioner
Mar 18, 2010 | Goodman CKL36AR36 Air Conditioner
Oct 09, 2008 | Goodman Heating & Cooling
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
Apr 27, 2016 | Honeywell Programmable Thermostat Heater
73 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: