Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You can turn off the Thermostat, and the powers switch on the furnance and turn the breaker off in the breaker box wait about 20 - 30 minutes and turn the breaker back on, and the power to the furance back on and the thermostat, this should reset the system.
Posted on Oct 04, 2009
there is no fuse on your condensing unit outside. pull the disconnect to kill the power to the unit and take off the removable panel above the 2 service valves. there will be an oval shaped capacitor that is marked herm and fan. there will be a rupture disc on the top that may have ruptured. also inspect the low voltage wiring(will still be hot unless you turn off the switch at your furnace). this low voltage wire operates a magnetic coil on the bottom of the contactor that closes a high voltage circuit to the fan and compressor.
Posted on Dec 15, 2009
Please specify the make and model of your unit.
If this is a LG inverter model.
The six flashes of the indoor unit light indicates a CH 06 alarm.
This alarm state indicates that the indoor unit pipe temperature sensor has measured a temperature out of range or the unit is protecting itself from this low temp state. Indoor unit coil temperature to low. Should it have reached a temperature of -5°C for longer that 30sec it will switch the machine off.
It could indicate that the unit refrigerant charge is too low or the sensor has gone out of calibration.
It should measure 5kΩ @ 25°C
Posted on Mar 22, 2010
Tips for a great answer:
Nov 02, 2015 | Carrier Heating & Cooling
May 26, 2015 | Heating & Cooling
Oct 24, 2014 | Senville 18000 BTU Ductless Air...
Aug 01, 2013 | Heating & Cooling
Aug 03, 2011 | Goodman CKL49AR49 Air Conditioner
Jul 16, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Feb 05, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Jan 29, 2009 | Heating & Cooling
Sep 03, 2007 | Carrier 38CKC036 Air Conditioner
40 people viewed this question
Usually answered in minutes!