Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hopefully there are markings on the old t-stat as to what terminal is what.
on the honeywell 8000 use the heat pump labeling and then the standard wiring would be
There should not be a bare wire, it probably just has the insulation stripped back way too far.
You should probably open the furnace and compare the terminal label in the furnace to the wire color. normally yellow and blue pass through the furnace and are wire nutted to wires going to the outdoor unit. In the furnace the white wire will connect to the w or w1 terminal. also, you will need to set the Honeywell stat to have the following parameters.
other parameters that I did not specify, you may read the manual and make your own decision but I recommend factory settings for the other parameters
Posted on Jun 18, 2008
Wire nut or tape the black off. The red is normally 24volt supply power to the t-stat. Blue may or may not be the common. Have a voltmeter?
Posted on Jun 24, 2009
Tips for a great answer:
Jan 23, 2014 | Nest Learning Thermostat 2nd generation
Aug 03, 2011 | Ruud UAKA037 Air Conditioner
Oct 24, 2010 | Heating & Cooling
Jul 26, 2010 | Ruud UAKA042 Air Conditioner
Mar 01, 2010 | Ruud Central System Air Conditioner
Jan 04, 2010 | Ruud UBHC Air Conditioner
Nov 04, 2009 | Ruud UBHC Air Conditioner
Sep 23, 2009 | Ruud UBHC Air Conditioner
Aug 10, 2009 | Heating & Cooling
73 people viewed this question
Usually answered in minutes!