Question about Comfort Products Heating & Cooling
Heat pump takes from 1 to 10 trys to bring the compressor on. When it does come on it is really noisey and runs forever before the stat is satisfied. Stat is in a ok place where it senses the whole house and out of the sun. I think the problem is the dual capacitor for the fan and compressor, the fan has no problem coming on. Could you give me some other things to check?
Do the thermostat have a time delay on it? most digital ones do you may have to get one if thats the case. Also are there start components on the unit? I've had top add them due to the newer units hasve nonbleed txv's and have a hard time starting up because of them. ans if oyu can see if there's a crank case heater on the unit becaause refrigerant migrates to the coldest spot and the compressor can have all the refrigerant inside of the can mixed with the oil. goof luck
Posted on Jan 12, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 11, 2014 | LG LP153HD3A - 14,300 BTU, R410A, 9.4 EER,...
Jun 01, 2017 | Heating & Cooling
Feb 11, 2011 | Carrier 38CKC036 Air Conditioner
Jan 27, 2011 | Heating & Cooling
Jan 12, 2011 | Ruud UAPA024 Air Conditioner
Dec 21, 2010 | Heating & Cooling
Jul 12, 2010 | Goodman CLQ36AR49 Air Conditioner
Dec 26, 2009 | Heating & Cooling
Nov 22, 2009 | Dehumidifiers
Aug 27, 2008 | Saunacore Special Edition Residential...
47 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: