Question about Heating & Cooling
Sounds like the thermostat is set up to control the fan with a call for heat(usualy the way we set up a heat pump system) New thermostat?
Posted on Jan 11, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 19, 2016 | Carrier Heating & Cooling
Feb 10, 2013 | Goodman Manufacturing Goodman...
Jan 26, 2011 | Goodman CACF048B2A Air Conditioner
Jan 25, 2011 | Heating & Cooling
Jun 02, 2010 | Goodman CKL42AR42 Air Conditioner
Dec 06, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 01, 2008 | Goodman Heating & Cooling
Nov 30, 2008 | Heating & Cooling
Oct 25, 2008 | Heating & Cooling
If the exhaust comes off the top of the furnace, you will need to make sure the condensation will drain all the way back to the condensate outlet found at the base of the inducer blower. If you are having to remove the tube from the pressure switch, there must be a blockage from the inducer down to where ever it drains to. Check to see if all tubes are free of blockages and if there is a condensate trap, clean it out. If the pressure tube you mentioned is facing up toward the blower allowing water to flow into it, reposition it so water will not enter the tube.
Oct 17, 2007 | Ruud UAKA030 Air Conditioner
63 people viewed this question
Usually answered in minutes!