- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Call a store that sells gas heaters and ask them.
Since most stores sell only a few models, you may have to call several before you find one that sells that particular brand.
You might also call your local gas company for assistance, they may also know.
God bless your efforts.
The furnace may be locked out on a fault, go to the furnace & see if there is a peephole window so you can see if there is a flash code. If so, count the flashes and the model & serial number along with the brand name so we can better stermine what may be going on.
double check your wiring. R terminal on the furnace will provide 24 volts to the t-stat. W terminal in the t-stat will send 24 volts back to the furnace W terminal to turn on the heat. G terminal in the t-stat will send power to the G terminal in the furnace when the t-stat is switched to fan on. Y terminal in the t-stat will send power to the Y terminal in the furnace which in turn will send 24 volts to the A/C outside. The C terminal in the furnace should be connected to the c terminal in the A/C outside as well as to the T-stat. Check the fuse again
check the wireing to the window motor an at the conector as well where it comes thru the door =- i have seen them break there an its covered === also check the circuit breaker in the fuse pannel position number 16 in the breaker for the window motors ok