Question about Hardware & Accessories
Copy following link for replacing single-pole switch with single pole 15086 / 15071 GE timers.
Copy following link to identify GE timer:
Copy following link for GE 15312 single-pole and 3-way timer
Posted on Nov 30, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The wires on your new switch are intended for black = power .. white = neutral . and red = lights .. with two black wires on the old switch I am assuming that there is a bundle of white wires in that wall box, the white timer needs to join that bundle ... then you need to determine which black wire is the power from the electrical panel ( voltage tester) and connect to the black timer wire .. the red timer wire connects to the other black wire in the wall..
Please Vote !!
Posted on May 13, 2010
SOURCE: I bought Utilitech #0141224 7
Hello, I bought an in door smart digital timer (G.E.) or Jasco product for my front porch light. I hooked all the wires as instructed and programmed according to instructions. I have a two wire system, so i left the green wire unattached. The light comes on but flashes very fast. What's up with that? This is the second one i've replaced, the first one did the same thing!. Whats wrong?
Posted on Sep 13, 2010
Find the Hot wire:
Your switch has 2 wires. One of these wires is Hot, and one goes to load. Disconnect wires from switch. Turn on power. Do not stand on wet surface. Test each wire to bare copper wire. When tester lights up, that is Hot wire. The other wire goes to load.
Hot wire goes to Black timer wire
Wire to load goes to Red timer wire
White wire connects to white wires that are twisted together
Bare copper wire connects to Green wire from timer
How to connect white wire to white wires that are twisted together.
a) Strip white timer wire so you have 1-1/2 " of bare wire. Stranded wire will wrap around other wires easily.
b) Remove wire nut. DO NOT UNTWIST wires.
c) Hold all whites together so bare copper lines up. Wrap stranded copper around the twisted wire.
d) Replace wire nut, or use larger wire nut. Twist real tight. Do not use tape. You can solder the connection.
e) When done, pull on white time wire to make sure it is held tight. Push whites back into box.
Posted on Sep 26, 2010
SOURCE: installing a GE digital wall
Black goes to Hot wire from breaker box
Red wire goes to Load (light, fan, motor)
White wire goes to Neutral
Green to bare copper ground wire
Your original switch had 2 wires plus bare ground.
One of these wires is Hot, the other goes to Load.
You said original wires are Red and Black
How do you find Hot wire?
-Your original switch had 2 wires.
-Remove timer from box.
-Pull original 2 wires out where you can test them
-Turn on power
-Use regular tester
-Tape tester leads to wood sticks so your hands stay away from voltage
-Power is on
-Test each original wire to bare ground wire
-When tester lights up, that is Hot wire ... this wire connects to Black wire on timer
- The other wire goes to Load so it connects to Red wire on timer
How to test for Neutral wire
Test Hot wire to your white wires - No need to untwist them.
When tester lights up, that is Neutral
White wire from timer connects to Neutral.
Green goes to ground wire.
How to reset timer
I'm not sure which timer you have. Probably GE 15086. Reset is small round button below HOUR button. Use paper clip and push-in reset until timer flashes 12 o'clock.
Posted on Sep 30, 2010
SOURCE: I bought Utilitech #0141224 7
If your box contains 2 and only 2 wires, then the Utilitec timer will not work.
You need the Intermatic ST01C or EJ500 timers that operate with a battery.
I have tested the Intermatic and Utilitec timers:
Do not connect white and red wires together on any timer, but thank you for solving the problem why lights blink when connecting timers.
Now lets look at your wires.
Scrape paint off the wires so you can identify white and black.
According to your information, the black wire inside box will connect to timer-black wire.
The red wire always goes to Load (your light, fan, motor)
The white wire is necessary to complete a circuit so the clock inside timer will operate.
The timer has a clock just like your alarm clock, and it needs to connect back to neutral busbar in breaker box.
This is why the battery-operated timers will work with two wires, the clock runs on battery.
The Utilitec timer-white wire is the wire that goes to Neutral
The timer-white wire is supposed to connect to the other white wires that are twisted together and covered with a wire nut ... but some boxes do not have this neutral wire
To work-around, the timer-white wire can also connect to a bare ground wire.
The bare ground wire also connects to Neutral busbar in breaker box
If you do not have a neutral or ground wire as described above, then you need the battery-powered ST01C or EJ500 Intermatic timers.
See if you can pull some more of the wire into your box ... there might be a ground wire that was cut off and pulling more wire might reveal a ground wire. This will salvage the project.
Aplus is one of many places that sell the Intermatic timer
For more about electric wiring:
Posted on Oct 24, 2010
Tips for a great answer:
Sep 16, 2014 | Dryers
Aug 13, 2011 | Whirlpool Dryers
Jul 28, 2011 | Maytag MDE9700AYM Electric Dryer
Jun 25, 2011 | Garden
Mar 08, 2011 | Jasco GE 06685 24Hour Mechanical Timer...
Feb 22, 2011 | Dryers
Jan 01, 2010 | Kenmore Dryers
Dec 20, 2009 | Whirlpool Dryers
Aug 17, 2009 | Dryers
Feb 14, 2008 | Dryers
208 people viewed this question
Usually answered in minutes!