Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: I have just had installed
F-6 High discharge coil temp. due to over charged /condenser coil blockage/less rpm of fan motor in out door/non-condensable gas.
Purge out over charged gas/clean condenser coil/Replace fan capacitor./Release all gas and flush out the system,replace filter drier and vacumise & do gas charging.
Posted on Dec 18, 2010
Tips for a great answer:
May 09, 2017 | Dishwashers
Jul 18, 2015 | Televison & Video
Sep 09, 2014 | Electrolux Heating & Cooling
Mar 04, 2014 | Televison & Video
Jan 09, 2014 | Heating & Cooling
Jan 11, 2013 | Heating & Cooling
Dec 18, 2010 | Heating & Cooling
Dec 30, 2008 | Panasonic PT-47WX53 47" Rear Projection...
247 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: