Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have just had installed
F-6 High discharge coil temp. due to over charged /condenser coil blockage/less rpm of fan motor in out door/non-condensable gas.
Purge out over charged gas/clean condenser coil/Replace fan capacitor./Release all gas and flush out the system,replace filter drier and vacumise & do gas charging.
Posted on Dec 18, 2010
Tips for a great answer:
May 09, 2017 | Dishwashers
Jul 18, 2015 | Televison & Video
Sep 09, 2014 | Electrolux Heating & Cooling
Mar 04, 2014 | Televison & Video
Jan 09, 2014 | Heating & Cooling
Jan 11, 2013 | Heating & Cooling
Dec 18, 2010 | Heating & Cooling
Dec 30, 2008 | Panasonic PT-47WX53 47" Rear Projection...
159 people viewed this question
Usually answered in minutes!