Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
look on the indoor unit and see what they do you hav common from trans former yellow for compressor white for elect heat then reversing valve usually orange green for fan on the out door unit board you can tell what is common and what is for heat
Posted on May 09, 2009
SOURCE: Heatpump A/C not working
First,Turn on the heat cycle (Not Emergency)and see if the outside unit come on,If not,and you don't have low voltage outside,Go to the inside unit and test the transformer,If you have low voltage from the transformer but not outside,It is the low voltage wires,If you don't have low voltage from the transformer,It's the transformer.If you have low voltage outside when in heat mode,but the unit won't come on,It's the contactor.Let me know if you need more help.
Please take time to rate this fixya
Posted on May 13, 2009
Tips for a great answer:
Feb 20, 2018 | Heating & Cooling
Feb 03, 2017 | Honeywell Heating & Cooling
Feb 27, 2015 | Carrier 52CQ-312-4 Comfort Series Heat...
Feb 26, 2015 | Heating & Cooling
Mar 01, 2017 | Haier Energy Star ESA3183 Air Conditioner
May 08, 2011 | Dometic Heating & Cooling
Sep 20, 2009 | Heating & Cooling
Jun 30, 2009 | Honeywell Electronic Programmable...
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 05, 2009 | Carrier 38CKC042 Air Conditioner
56 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: