Question about Water Heaters
2 things to check one to make sure you are not picking air from tank dis-connect the inlet side only of the feed and rig you a hose or copper tubing inserted into a gallon can or bucket full of oil , try to run off this must bleed as before if it does pulling air from tank , if not and while bleeding you get the same on load sound from the motor then check this , between the motor and the pump there is what is called a boot coupling that transfers power from the motor to the pump most of these are rubber and with time and heat will sometime allow the drive in the ends to rotate internally cheap part usually $9 before replacing hold the old one against the new mark and cut the exact length as the old one , match the end you need with the same end that come off old one as these kits come various parts for different hookups , also a leak in the line will also cause same symptoms ck as much of the line as possible for damage , try these and get back with results and if no fix will try to assist further
Posted on Jan 11, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 18, 2015 | Water Water Heaters
Oct 28, 2014 | Rheem 50 Gallon FVR NATGAS Water Heater...
Mar 21, 2014 | Water Heaters
Feb 01, 2013 | Rheem Paloma PTG-74PVN / RTG-74PVN...
Jan 22, 2011 | Water Heaters
Jan 14, 2010 | RTO Home Heating Products 5.5HH240...
Dec 29, 2009 | Rheem Paloma PTG-74PVN / RTG-74PVN...
Jan 28, 2009 | RTO Home Heating Products 5.5HH240...
273 people viewed this question
Usually answered in minutes!