Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: only fans work on split
Does the compressor try to start and the shuts off or is the breaker slamming off as soon as it is turned on. If it takes a few seconds the comp could be locked up and trying to start, high amps and tripping breaker. Tripping breaker right now would indicate a shorted or grounded compressor. Really would need to be ohmed out with a meter to check for ground. Not good either way.
Posted on Apr 25, 2008
Check your filters, dog hair and lack of maintenance will definitely burden the cooling mode of the Mr Slim units.
Posted on Aug 24, 2009
Tips for a great answer:
Dec 19, 2015 | Fujitsu 9RLS 9000 BTU Split System Air...
Apr 12, 2013 | Heating & Cooling
Dec 12, 2010 | LG LS-K2430HL Heat Cool Mini Split Air...
Aug 27, 2010 | Fujitsu Heating & Cooling
Nov 28, 2009 | Coffee Makers & Espresso Machines
May 25, 2009 | GE Zoneline AZ38H12DAD Split System Air...
16 people viewed this question
Usually answered in minutes!