Question about Heating & Cooling
I would start with some basic maintenance shut off. open front pannels vacuume out all accesable areas.use a plastic nozzle with a paint brush to loosen dirt.Change or clean filtration system follow manufactures cleaning procedures.Oil the bearings on blower motor and squirel cage.Then visually inspect any arking witness marks for loose connections.Start it up and listen for improvements.
Posted on Nov 28, 2012
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Yes you are right the control voltage of your furnace is 24 volts. Really without a load on the transformer usually runs 28 volts then you put a load on it and it drops down to 24-26 volts. Check the voltage between the R terminal and the W terminal with the selector switch in heat mode. Or move the thermostat switch to heat. R to C would do it also. You could also do the voltage check right at the transformer one side of the transformer is 120 volts and the other side is 24. Look for the black and white wires that is the 120 volt side the blue and yellow or off colors is the secondary side.
Now if it checks low say 24 or 22 your gas valve needs min. 24 volts to hold open the valve that allows the gas to flow into the burners. So if one of the symptoms is related to burners come on for about 3 to 5 min. then shut down and the fan keeps going it is loosing the necessary voltage to hold open the gas valve.
One more thing make sure the air filter is clean as this will cause the heat to build up in the heat exchanger and hit the high limit safety device and cut the gas off. Until the air cools enough to allow the high limit to reset then the gas valve will open and start the process all over again. Dirty A-Coil will do the same thing as the air goes through the coil to get to house. let me know how it goes ken
Posted on Jan 18, 2009
On the thermostat if its a manual on then pop the cover off and look for a small dial with numbers on it. Take and move it tpoi a higher number than whats it is set at. Its called a heat anticipater and is supppose to make it so that the unit does not oveshoot or under shoot like what your experiencing. If its a digital oine then you are going to have to configure the setting in the insdtallers menu.
Posted on Dec 21, 2008
I would insist that Sears either have a Senior tech come out and fix it or return it to the state it was prior to them touching. Then call some one else. Have them involve the Goodman rep in your area.
Posted on Jan 20, 2009
unfamiliar with watt restrictors.
heat strips have 2 safety devices, a thermal overload, they get to hot they shut off, cause not enough air flow increase fan speed this device is auto reset. a fusible link a fail safe to thermal over load, no reset and sometimes replaceable. if this does not help would like to ask you a few questions. one of the buildings i take care of has 200 + reem/ ruuds all electric heat. if a part is defective replace, please do not by pass. safety frist.
Posted on Mar 07, 2009
verymuch so it is clogged up , now open system treat drain pan with bleach ,blow out two lines if there are available but if theres only one treat that on ,then treat the coils clean an treat them after cleaning pour little bleach in the bottom of the pan
Posted on May 24, 2010
Tips for a great answer:
Apr 07, 2016 | Microwave Ovens
Dec 08, 2015 | Williams Heating & Cooling
Nov 16, 2014 | Heating & Cooling
Aug 24, 2014 | Heating & Cooling
Jun 08, 2017 | Heating & Cooling
Jun 18, 2017 | Heating & Cooling
Oct 24, 2010 | Dayton Gas Furnace Heater
Aug 18, 2010 | Intertherm Heating & Cooling
Jan 27, 2010 | Honeywell Electronic Programmable...
Jan 19, 2010 | Honeywell Electronic Programmable...
449 people viewed this question
Usually answered in minutes!