Question about Procom QL300TYLA Heater
Pilot & gas system shuts down after a few minutes, we reset pilot it runs an then shut down again...
90% of the time, this problem is caused by either a clogged gas orifice on the pilot light's gas line, or by dust/debris in the pilot air intake, as stated by tradesman1. Start by blowing compressed air through the pilot air intake, both directions. If that doesn't solve the problem, remove the pilot assembly, then the pilot orifice, and blow compressed air backwards through the small orifice. The bottom line is that anything that causes the pilot flame to reduce in size will trigger the oxygen depletion system and that will result in the unit shutting itself off. This is a safety measure. Other possible causes: insufficient gas pressure to the unit, high altitude, defective thermocouple.
Posted on Jun 11, 2009
I had this same problem and the only thing that I found was a small spider web in the pilot air intake which had traped a small piece of lint I blew this out and the heater worked great
Posted on Jan 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 05, 2015 | World Heating & Cooling
Dec 23, 2010 | Procom ML300EBC Heater
Jan 19, 2010 | Heating & Cooling
Jan 10, 2010 | Dayton Gas Furnace Heater
Dec 31, 2009 | Vanguard International VN18B Infra-Red...
Nov 12, 2009 | Dyna-Glo RMC-8001SS Heater
Feb 13, 2009 | Cozy Enclosed Front Console Heater 70,000...
Jan 28, 2009 | Rinnai Desa Vent-Free Infrared Gas Heater:...
Jan 20, 2009 | Heating & Cooling
Jan 07, 2009 | Procom (177653) Utility Heater
608 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: