Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
First check your circuit breaker or fuse that supplies power to the outside unit. It's probably separate from the inside unit. Then try to turn unit on. If the fan and compressor just make a humming sound then turn it off and check the capacitor if you have a multimeter. You can also look at it and see if the top looks expanded. That's a good sign its bad, but not all bad one's look expanded. Tomorrow I will have access to an LG service manual and can let you know what the code means. Sorry I can't get it sooner. Let me know what you find.
Posted on May 03, 2010
SOURCE: my hitachi ductless split room
please reset you air conditioner by it,s remote to heat mode and check thermostat setting maybe it has been turn off after remove air conditioner,s electric supply plug from electric source . i hope after reset it will be able to work again.
hope answer the question
Posted on Oct 03, 2010
SOURCE: The Wall unit to my
If the unit displays Error E4
1)Check whether the winding resistance and
operation current of the compressor are normal.
2)Check whether the high and low pressure is normal
when the unit is running.
3)Check (whether the coil pipe sensor is normal)
whether the contact of the inserted on the circuit
board is well, the coil pipe temperature sensor is
fixed, the evaporation of the indoor unit is well,
the key is to check the evaporator temperature
detected by the coil pipe temperature sensor has
reached the cooling or heating temperature.
4)Check whether the surface of the condenser is too
dirty, it should be cleaned when it is too dirty.
5)Check whether the capacitance of the outdoor motor
and the fan is damaged, it should be replaced when
it is damaged.
6)If the above items are normal, the electric control
board should be replaced.
Please do rate the solution if the issue is resolved or post a comment for further assistance.
Thank you for using fixya have a nice day:-)
Posted on Jan 11, 2011
Tips for a great answer:
on Dec 04, 2009 | Heating & Cooling
Jun 18, 2014 | Samsung AQV36JA Classic 36000 BTU Single...
May 26, 2014 | LG LMN127HVT LMN127HVT 12 000 BTU Ductless...
Jun 04, 2017 | GE Zoneline AZ38H12DAD Split System Air...
Jul 21, 2011 | Heating & Cooling
May 02, 2010 | LG LA185HV Split System Air Conditioner
Nov 12, 2009 | Kitchen Ranges
Mar 07, 2009 | Soleus KFR12GWD 12,000 BTU Heat & Cool...
Jan 02, 2008 | GE Quiet-Aire Ductless Split System Air...
81 people viewed this question
Usually answered in minutes!