Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I have had this problem many times. If changing the flame sensor and cleaning the front of the venturi tube did not help. Also check the ground wire that is attatched to the burner assembly. Also, I have found it necessary at times to replace the wire completely from the flame sensor to the ignition board (circuit board). if you have a multi meter that is capable of reading micro amps, put it in series with the flame sensor and you should see 3-5 micro amps dc. If this is not present, check and make sure that the flame is covering the sensor fully.
Posted on May 17, 2009
Good one! Is the flame getting to the flame sensor within the few seconds? Maybe a good cleaning of the burners or flame tray would help. 1.3 ma is enough for the flame rod to tell the board to stay on. Re-do all the ground connections both at the board and furnace cabinet to be safe. Check the polarity of the power going to the furnace. What are the chances the second board is bad?
Posted on Jan 15, 2010
Tips for a great answer:
Dec 03, 2016 | Carrier Heating & Cooling
Nov 04, 2013 | Carrier Weathermaker 8000 Gas Furnace 125k...
Apr 22, 2013 | Heating & Cooling
1. Thermostat calls for heat.
2. Draft inducer motor starts.
3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes.
4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution: You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. Please see "limits, rollout switches & furnace control boards" further down on this page. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Nov 25, 2010 | Heating & Cooling
Oct 18, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 03, 2010 | Dayton Gas Furnace Heater
Dec 24, 2009 | Carrier Heating & Cooling
Oct 06, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 17, 2009 | Carrier 38CKC042 Air Conditioner
Jun 27, 2008 | Carrier 38CKC042 Air Conditioner
Sep 25, 2017 | Heating & Cooling
Sep 25, 2017 | Heating & Cooling
182 people viewed this question
Usually answered in minutes!