Question about Cross Furnace Draft Inducer Blower 115 Volts Fasco # A064
I have a Heil furnace and when it tries to come on within a second or two of trying to come on it goes into lock out mode. The computer board, limit and roll out switch have been replaced what is causing this problem
Check your exhaust and your inducer
if your inducer cant not sence proper air flow
either positive or neg depending on your set up
it will shut down and lock out on safety
Posted on Oct 06, 2009
Pressure swithc stuck closed? try undoing on of the wire going to the pressure switch and see if it stays on longer. Make sure you tested all limit switches there are usually at least 3 and up to 5
Posted on Jul 27, 2009
Sound like a thermocouple, or flame sensor.
If it has flame sensor make sure you check micro amps to verify operation, because it might be the board that controls the sensor.
Posted on Dec 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 22, 2014 | Honeywell ICP Tempstar Heil Furnace Gas...
Oct 28, 2013 | WHITE-RODGERS DIV White Rodgers 767a-361...
Oct 19, 2013 | Fasco ICP Heil Tempstar Furnace Inducer...
Oct 17, 2013 | Carrier Icp Heil Tempstar Furnace Blower...
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Mar 04, 2011 | Honeywell International Heil Quaker...
Dec 30, 2010 | Water Heaters
Nov 11, 2009 | Heating & Cooling
Oct 17, 2009 | Heating & Cooling
Oct 07, 2010 | Cross Furnace Draft Inducer Blower 115...
929 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: