Question about Fahrenheat Ceiling-Mount Industrial Heater - 7500 Watt
The diagram in the manual shows 3 wires black white and ground, the wire I used has 4 (black red white and ground) what do I do with the extra wire?
If you use the white wire as a hot wire, you must identify the wire as being a hot wire at the breaker panel and the unit. The white
wire must be marked about 6 inches back from the terminal
connections with black paint or wrapped with black insulation tape.
It would be easier to use the red wire, since most electricians would identify it as being a hot wire
Posted on Jan 04, 2010
As long as the red wire isn't wired to anything just use the white black and ground. Cut the red wire at both ends short or tape each end of the red and leave in the box.
Posted on Jan 09, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 09, 2011 | Leviton 1755 Triple Rocker Switch Decora
Dec 18, 2010 | 1996 Jeep Grand Cherokee
Jul 28, 2010 | Dryers
Jan 01, 2010 | Fahrenheat Ceiling-Mount Industrial Heater...
Nov 17, 2009 | Cobra 29 LTD CB Radio
Nov 09, 2009 | Fahrenheat Built-In Baseboard Thermostat...
Jul 04, 2009 | Sony CDX-GT210 CD Player
Mar 22, 2009 | Fahrenheat Electric Hydronic Baseboard...
Jul 04, 2008 | Dayton Electric Heater
692 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: