Question about Electric Circuit Breaker Kit for Furnace
The power wire is heating up
60 amp breaker on furnace and at box
can i use 30 amp breakers
how can i fix this
You should have a 3- conductor # 6-3 copper wire running to this 60 amp breaker @ the furnace to the panel if this is not the case you should replace this with a # 6 as of now as it is a fire hazard as it is and needs to be fixed at once , # 10 -2 wire is only good for 30 amps and a 60 amp breaker will not trip under fault condition and you could have a fire , if you need further assistance on this let me know and i will try to help
Posted on Jan 10, 2009
Tips for a great answer:
Jan 06, 2014 | Circuit Breakers & Wiring Panels
Nov 04, 2012 | Bryant Westinghouse Bqc Quad Circuit...
Oct 31, 2012 | Circuit Breakers & Wiring Panels
Oct 27, 2012 | Circuit Breakers & Wiring Panels
Nov 11, 2010 | Electric Circuit Breakers & Wiring Panels
Nov 08, 2010 | General Electric 100Amp 3-pole circuit...
Oct 31, 2010 | Sylvania Circuit Breaker
Jul 19, 2010 | Challenger Connecticut Electric UBITB-A230...
578 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: