Question about Heating & Cooling
Hi, i need to remove and relocate 12000BTU split air conditioner without releasing gas (if possible) from the system without calling a contractor to regas the unit. I am very technicaly minded, i installed the system myself without any problems 1 year ago.
Tech. assistance in this matter would be highly appreciated.
The simplest way of explaining this is as per the following. On your outdoor compressor unit there should be two pipes, one smaller diameter [high pressure] and a larger diameter pipe [low pressure]. Turn your A/C on inside the house and then shut off the smaller diameter pipe. Run the unit for a around 3 to 4 minutes and then check if the cooling is reducing from the unit inside the house. When you feel room temperature air [not cool] being emitted from the indoor unit shut off the larger diameter pipe and turn off unit. Isolate electrics, disconnect A/C piping and immediately seal the piping with good quality tape to prevent egress of dirt. When re-installing a quick purge of gas is usually only required to clear the lines if they were sealed properly and kept clean. Ideally running a vacuum pump is recommended but if care was taken then it may not be needed, as in many of my installations.
Posted on Nov 13, 2009
If the unit has king valves you can close the liquid line and pump the refrigerant into the condensing unit. Do not pump the unit into a vacuum. Any remaining refrigerant should be properly recovered by a EPA licensed tech.
Move the unit, reconnect (taking care not to allow any moisture or contamination into the lines) and evacuate the refrigerant lines and the evaporator down till it holds 500 microns for 10-15 minutes.
The refrigerant can then be released back into the system.
Hope this helps.
Posted on Jan 09, 2009
Matt is correct! your compressor could possibly be a scroll. DO NOT RUN THIS INTO A VACUUM!
Posted on Mar 05, 2015
Testimonial: "Thanks a lot for the info, helped a lot though, better late than never. Regards Phillip"
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 15, 2015 | Turbo Air Inc Turbo Air Ductless Mini...
Jan 16, 2014 | Turboair TAS-24H Split System Air...
Apr 05, 2013 | Heating & Cooling
Feb 01, 2011 | LG LS-L1210CL Mini Split Air Conditioner
Dec 25, 2010 | Heating & Cooling
Oct 12, 2010 | Coleman Mach III Air Conditioner
Jul 15, 2010 | Carrier 38CKC060 Air Conditioner
Jun 05, 2010 | LG LSC121PMA Split System Air Conditioner
Jun 30, 2009 | LG LSC121PMA Split System Air Conditioner
Mar 25, 2009 | LG LS-L1210CL Mini Split Air Conditioner
30,478 people viewed this question
Usually answered in minutes!