Question about Fujitsu 24C1 Air Conditioner
Help! My air conditioner is leaking water into the room. Any ideas?
during Cooling and Dry modes, if the unit is used under conditions of
lower temperature (18C) the heat-exchanger may freeze, leading to water leakage and other damage.
If the unit is used for long periods under high-humidity conditions, condensation may form on the surface of the indoor
unit, and drip onto the floor or other objects underneath. (About 80% or more)
Increase Temp to 20 and also run coil dry cycle,
Posted on Jan 23, 2009
Yes I do. My units were leaking. I had an aircon tech come out and clean the blower. I was full of mold. It is not an easy task. Most aircond techs don't want to touch these units. Each machine took about an hour to clean. I am so glad that I had that done, now the house smells cleaner. Inge
Posted on Oct 30, 2010
Is it a split system? I had the same problem with my split system and and it was because the condenser line was mounted wrong. The line was mounted so the water had to go uphill and it was causing the condensation to leak through the front of the unit.
Posted on Aug 14, 2007
Try cleaning the filters?
Posted on Jun 08, 2007
Make sure the unit is level, this is very important. Check for blocked drain tube, which runs from the bottom of the drain pan under the cold coil to the outside. Clear tube with a piece of coathanger wire, be gentle.
Posted on Jul 15, 2007
Tips for a great answer:
Nov 03, 2013 | Fujitsu ASU12RLS2 Wall Mounted Indoor Unit...
Jul 11, 2011 | Fujitsu 24R1 Air Conditioner
Feb 01, 2011 | Fujitsu 24C1 Air Conditioner
Dec 26, 2010 | Fujitsu Air Conditioners
Mar 12, 2010 | Fujitsu 18C1 Air Conditioner
Feb 01, 2010 | Fujitsu 24C1 Air Conditioner
Nov 08, 2009 | Fujitsu 24C1 Air Conditioner
Jul 02, 2008 | Fujitsu 18C1 Air Conditioner
Jun 03, 2007 | Fujitsu 24C1 Air Conditioner
1,913 people viewed this question
Usually answered in minutes!