Question about Air Conditioners
Goodman Dependable 92 blowing cold air only
Blowing cold air on this furnace usualy caused by high limit trip, or flame roll out. the first one, (high limit) is from insf. air flow. (blocked filter,bad zone damper?
The second,(flame roll out) caused by bad heat exchanger,blocked vent.ect.
Posted on Jan 11, 2009
Tips for a great answer:
Aug 08, 2015 | Goodman Air Conditioners
Oct 09, 2014 | Goodman Manufacturing Goodman...
Nov 11, 2013 | Goodman Manufacturing Goodman ARUF486016...
Jul 18, 2010 | Goodman Air Conditioners
Jan 08, 2010 | Goodman CLQ36AR49 Air Conditioner
Jan 07, 2010 | Goodman Air Conditioners
Dec 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Aug 30, 2009 | Goodman CLJ30AR32 Air Conditioner
Mar 17, 2009 | Goodman Air Conditioners
429 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: