Question about Goodman GDS80703ANA Open Flame Mid-Size Heater
Sometimes my gas good man furnace starts running then like after 20-30 seconds everything shuts down. I changed the flame sensor with a new one and I still have sometimes the same problem. After that I turn the power switch off then on. It starts working again. Is there any reason why this is happening? Anything I can do to fix it? The furnace is only 6 years old.
The two most common reasons I have found for this are listed below. You have already addressed the third one.
1) Grounding issue. This can be difficult to find but easy to diagnose. Try using a volt meter or even just a piece of wire. Touch one end to an unpainted surface of the interior furnace cabinet and the other end to the sheet metal plenum or other ground. If the symptoms go away then you have diagnosed the problem and need to find the faulty ground.
2) Pressure in the flu. Check to make sure that the flu vent pipe is not clogged or even partially filled with debris. The small rubber hose that connects to the switch from the inducer blower motor may be clogged. Also check the orifice on the inducer motor side. You can clear this with a paper clip. Water (condensation) in the inducer motor housing or pressure switch can cause a failure too. Rarely is the pressure switch itself bad. This usually will only happen if it has been physically damaged or soaked. Best of luck.
Posted on Jan 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 05, 2016 | Heating & Cooling
Oct 02, 2015 | Coleman Gas Fired Mobile Home Furnace,...
Jan 10, 2014 | Heating & Cooling
Oct 26, 2012 | Goodman Heating & Cooling
Oct 24, 2010 | Heating & Cooling
Feb 15, 2010 | Heating & Cooling
Dec 13, 2009 | Goodman GMS90703BXA Heater
Mar 11, 2009 | Carrier Heating & Cooling
Jan 16, 2009 | Heating & Cooling
Dec 21, 2013 | Goodman GDS80703ANA Open Flame Mid-Size...
Jan 29, 2012 | Goodman GDS80703ANA Open Flame Mid-Size...
877 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: