Question about Reddy Heater-170,000 BTU Kerosene Deluxe
Reddy heater ,has never been started ,, will not ignite
1st check to see if you have spark, 2nd check the pump pressure using the correct pressure gauge, the pressure should be 5.1 psi for model 115. if little or no pressure you may have a air line leak or a defective rotor. if you do have pressure you may have a plugged nozzle. i hope this helps.
Posted on Jan 26, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 24, 2010 | Desa International ReddyHeater® R115DT...
Oct 03, 2010 | Reddy HEATER R115 115,000-BTU PORTABLE...
Jun 08, 2010 | Reddy Heater-75-125,000 BTU Variable
Dec 29, 2009 | Reddy HEATER R115 115,000-BTU PORTABLE...
Dec 04, 2009 | Reddy HEATER R115 115,000-BTU PORTABLE...
Mar 05, 2009 | Reddy R115DT Oil Filled Utility Heater
Jan 15, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Dec 21, 2008 | Reddy Heater-70,000 BTU Kerosene w/T'stat
Dec 09, 2017 | Reddy Heater-170,000 BTU Kerosene Deluxe
135 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: