Question about Heating & Cooling
Water leaks from the base of the my GMPN furnace and none to little water flows through drain pipes.I check the drain pipes extend out of the furnace for any clogging . Pipes are clear.
Please help me out.
Check the drain tubes inside the furnace. There may be a loose connection or a split tube.
The unit could also leak from the gasket between the secondary heat exchanger and the vent fan housing. The secondary heat exchanger ould also be leaking or cracked.
Hope this helps.
Posted on Jan 08, 2009
Hey, thanks for the post about water leaks from your furnace. My sister had a problem and I haven't heard if she got the problem fixed. I think that hiring a professional might be the best option for her, but I'm not sure if it is a simple problem or not. http://www.dependableaircond.com
Posted on Jan 24, 2017
Water was leaking from the base of my HVAC furnace, and not from the drain hose as it had on other occassions. I blew out the drain hose, changed filters, etc etc. Finally paid a guy $100 to come out. In 30 seconds he fixed it. So I asked questions on HVAC maintenance for another 20 minutes just to get my money's worth in education.
The fitting between the furnace and the drain hose unscrews. Whereas I had pulled the hose off of the 90 degree angled, corregated fitting that looked to be permanently attached with a cement or putty, he easily unscrewed the whole fitting. The clog was in the 90 degree angle part. Detaching and cleaning the hose and fitting are now part of my Spring self-maintenance.
An honest HVAC service would have recommended that over the phone before scheduling the repair guy. It cost me $100, it cost the company a 4 year client. Found a better HVAC guy who works independently.
Posted on Feb 17, 2011
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 13, 2016 | Dayton Heating & Cooling
Feb 21, 2015 | Ruud Heating & Cooling
Feb 05, 2014 | AutoFlo 250 Humidifier
Aug 10, 2012 | Goodman Heating & Cooling
Jul 13, 2011 | Goodman GMS90703BXA Heater
Oct 02, 2010 | Goodman GMS90703BXA Heater
Aug 22, 2010 | Heating & Cooling
Feb 03, 2010 | Goodman Heating & Cooling
Oct 13, 2009 | Goodman GMS90703BXA Heater
1,471 people viewed this question
Usually answered in minutes!