Question about Jandy LAARS LX250 - PROPANE, DIGITAL READ-OUT, LOW NOX
I've had this problem for over 2 years on the Laars model LX250.
Several repairs were done by quailfied professionals licensed and trained techs. on the above unit and none had fixed the problem. Because of all the expenditures I paid, I fired the same company I been dealing with for many years. I did some homework on my own and found all I kept paying for was just for process and elimination work and useless labor done. I could'nt afford continuing paying and wasting money. Finally I did some homework on my owm and discovered some repairs were'nt necessary. My unit says "Service - AGS" code is still lit. "Hi limit 135F & 150F", "Harness high limit switch" "Flame sense rod" were all replaced. Filter cleaned, water flow and pressure check, pump working perfectly and gas flow all checked by new friend in the same field and "AGS" code is still lit. These techs all can't stay long enough to wait until they see the problem lit after 20 to 30 mins after each repair is done. I know, cause I've seen it for my self, they do not have the patience to wait and will charge me more to come back. What else can be done. PLEASE HELP. I'm about to pull this unit out.
Peter J. Berastain
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
AGS automatic gas shut down
which means you have ignition failure, which can be from low gas pressure, or volume. if the heater fires then goes out the signal is not going back to the control module check all wiring.
Posted on Jun 18, 2009
AGS stands for Automatic Gas Shutoff. This means the heater failed to sense a flame or flame rectification. When this occurs, the the gas valve will close as a safety precaution. The heater will have to be reset to get another call for heat.
Posted on May 19, 2010
Tips for a great answer:
Jun 29, 2015 | Jandy LAARS LX250 - NATURAL GAS, DIGITAL...
on Apr 19, 2010 | Jandy Laars Lt 250,000 Btu Heater
(automatic gas shut-down)
1. Oscillating pump pressure.
1. Clean filter or identify and repair cause of
2. Low gas supply pressure.
2. Identify and repair incorrect supply pipe size
or pipe line blockage.
Refer to qualified service
3. No flame at burners.
3. No flame at burners. 3. Identify and correct
loose wiring connections, or problems with igniter, flame sensor, gas valve,
or ignition control.
Refer to qualified service
info the manual is here:
May 03, 2011 | Jandy Laars Lt 400,000 Btu Heater
Jul 16, 2010 | Jandy Laars LX Pool Heater / 400,000 BTU /...
Oct 30, 2009 | Jandy Laars Lt 400,000 Btu Heater
Jul 16, 2009 | Jandy LAARS LX250 - NATURAL GAS, DIGITAL...
Jun 16, 2009 | Jandy LAARS LX250 - NATURAL GAS, DIGITAL...
Jun 06, 2009 | Jandy Laars Lt 250,000 Btu Heater
383 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: