Aprilaire 600: water only runs in "Emergency" Heat mode
I have a Aprilaire 600 humidifier. The problem is that water only runs through the humidifer only when the furnace in "Emergency/Auxiliary" Heat mode. Once the furnace is running under "Normal" heat mode, there is no flow of water through the hudifier.
I tested this by setting the house temperature very high, therfore, forcing the "Emergency" Heat mode. The humidifer work fine, i.e., the water flow is normal. However, once I turn back the heat to normal, the humidifier stops working..
An expert who has achieved level 3 by getting 1000 points
An expert that got 10 achievements.
An expert that got 5 achievements.
An expert whose answer got voted for 100 times.
Re: Aprilaire 600: water only runs in "Emergency" Heat...
When your unit is on normal the outside unit works and the inside only the fan runs. your heat pump does not remove any humidity when it operates so the installation cotractor did not wire it to operate then. you can change the wiring on the humidifier to operate all the time by wiring it to the fan (g) terminal then it should work just turn it all the way to the lowest humidity when you are in cooling mode.
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US. click here to Talk to a Repairman (only for users in the US for now) and get all the help you need. Goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Thank you for contacting us with regards to your model 600 Humidifier. The Change Water Panel indicator should flash when the control knob is set to the Test/Reset mode. The flashing indicates that the timer has been successfully reset. However, the humidifier should operate for the first 60 seconds of Test mode as long as your furnace is running. If your humidifier does not turn on, contact your installer. The humidifier may require service. We appreciate the opportunity to be of assistance. Sincerely,
Brett Phillips Technical Support Research Products Corporation
you need to make sure your humidity level in the house isnt higher then what your humidifier will provide at any givin outdoor temp. this chart is in the owners manual. you cant remove the wires going to the ODS or it will give an error unless you have a resistor to put in its place. Anyway if the humidifier works in test mode according to AA it works so you may have higher humidity than you think, the highest your gonna get is 45% as the temp outside drops it will allow less humidity so it doesnt cause window condinsation (property damage) here is a copy of the chart. the #s on the left are the dial setting
TABLE 2 – % Relative Humidity Guide
Outdoor Temperature (°F)
-10°F 0°F 10°F 20°F 30°F 40°F
1 10% 10% 10% 15% 20% 25%
2 10% 10% 15% 20% 25% 30%
3 10% 15% 20% 25% 30% 35%
4 15% 20% 25% 30% 35% 40%
5 20% 25% 30% 35% 40% 45%
6 25% 30% 35% 40% 45% 45%
7 30% 35% 40% 45% 45% 45%
if it works in the test mode then it should be okay but you can get a humidity gauge from radio shack and set in the house to see how high or low its is. the humidifier is only going to give a max of 45% humidity
You may need a HRV/ERV installed. Depends on your indoor air quality(IAQ). It may be allergies. I would talk to a reputable heating/cooling contractor in your area to evaluate your system, recommendations.
It is possible you may have wired it wrong. Make sure your humidifer is not robbing power from your thermostat. This would explain when your humidifer makes a demand to come on it robs power from your t-stat making it lose its call for heat. Wire your humidistat to the "w" terminal and the common terminal so it only runs on a call for heat. With the bypass type of humidifier you purchased it wont do you any good to run when the heat isn't running anyway. If you want an independent operation humidifier you need a steam type.
These units have simple configurations They have a water supply similar to a ice making referigerator, an enclosure connected to your supply duct that houses a prop fan and media, a seperate humidistat and a drain for excess water. Your unit may also include fancy controls including an outside thermometer & humidistat to avoid over humidification that can cause problems during freezing weather. The humidistat looks a lot like a thermostat and is located in your living space or in the return duct. The prop fan in the box pulls air from the duct, through evaporation media and back to the duct. An electric solenoid valve releases water that pours over the media.
If the humidiy is below the humidistat seting and the AC/heater is running, the Aprilaire fan starts and the solenoid valve opens. I suspect the facier controls include the flashing warning light.
The warning light spells problem. Aprilaire's customer service should be able to provide guidance for the homeowner in the form of simple checks. I suspect your contractor is avoiding a warentee call and the trip it requires.
A word of caution. These humidifiers can be powered directly from your air conditioning unit control board from an auxiliary connection. If the control board isn't rated to carry the current required by the Aprilaire fan, valve and controls or the Aprilaire encounters and electrical problem, the board can be damaged. This can be avoided by using a relay. The AC board switches a low energy relay. 120 volt house power is connected to load side of the relay and runs the Aprilaire.
My board cooked at a location near this connection, but I can't be sure that the load from the humidifier caused it since four of our neighbors also lost their board. It failed the evening of a snow storm and required a costly emergency after hours service call. The next day a new board required a three hour drive. Fortunately a fan powered propane heater kept our pipes from freezing.