Goodman PGB042100-1 REVA Flame sensor not working; no heat
Service technician came cleaned the sensor, got heat going again. Heat was off again shortly after he left.
Tehcnician says I most likely need to replace the primary circuit board at estimated cost of $636. (Should this cost this much?)
Also had service a few months ago for contactor.
Unit is 10 years old. Repair or replace?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need. goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
you could try check the AFC automatic fan control which brings the fan on temp rise and shuts off on temp fall, see if its clean on the back of it, check filters are clean try cleaning flame sencor , the afc inside the cover the temp dail turns back when cooling see if this sticking none of this will cost you, just time.
Hello, sounds like either a dirty flame sensor or open limit switch. First try cleaning the flame sensor by turning power off to the furnace and using some steel wool. If the flame sensor checks out good then you limit switch is opening becuase of lack of airflow. check air filter, clean blower wheel, and check to make sure the blower wheel is running at proper speed and not dragging sometimes cause by a weak capacitor.
I believe this code is ignition failure.
Turn power off and after 20 seconds turn power on with thermostat calling for heat.
Vent blower should come on first. After a bit igniter should lite up. You should hear click noise
of gas valve open up. If igniter does lite and you hear click noise, flame should come on for a few seconds minimum. If igniter doesn't lite and you hear click noise from gas valve, igniter is bad. If flame lites and then goes out, flame sensor probably needs cleaned.
Both igniter and flame sensor are in metal plate under burners. Igniter has 2 wire going to it and flame sensor has one wire. If you think it is flame sensor you can remove with taking it out with 1 1/4" hex screw. Flame sensor will have white film on it if it needs cleaned, clean with steel wool or a dollar bill.
If it isn't weither of these it is gas valve or circuit board.
Sounds as though your issue lies within the flame sensor.
The flame sensor senses that there is flame present once there is a call for heat. It sends its signal back the board or ICM and the furnace operates as normal. If no signal is sent, then the furnace automatically shuts down as a safety procedure. The furnace will attempt to light several times before shutting down on a fault code or lockout.
The number 1 reason for flame sensors to fail is they are dirty. Check the sensor for dirt build-up. Clean the sensor with a damp rag or a scratch pad. Inspect the grommets for crackings. Also check and clean all grounds. If this doesn't work, you will need to replace the sensor or call for a service technician to ensure the sensor is the only issue at hand.
If the hot surface ignitor comes on and fires the burners, and then shuts back down, you need to take a look at the flame sensor. It is a ceramic rod with a metal tip that rests in the pilot flame. When heated from burners, it sends a signal to the main control module, circuit board, which ever this unit is equipped with to keep the burners on. It is a safety to shut the burners down if there is a problem. Take some fine steel wool to clean the metal tip on this and this should take care of the problem. If this does not do it, then 99% of the time you have a faulty control board or module. It will have to be replaced.It is where this flame sensor connects.It will continue to drop out of the circuit, and the fan will start and run. You're T-stat is good or the Hot Surface ignitor would not glow. You will need to take as much info you can from the unit, Goodman and the control, all numbers with you.You can purchase this part at a appliance parts house, or air conditioning parts house. Please keep me informed, I would like to hear back from you. I hope this has given you some direction to follow.Good Luck, Shastalaker7
You can sand the flame sensor but it sounds like another problem. Sounds like a limit switch or something in the control circuit, You need to have a service tech look at this. Ask for free estimate on repair. I have worked on hundreds of these units and they are sometimes tricky to work on. Lenox has come up with new controls for the whisper heat furnace to replace the old ones. If the flame sensor is bad the unit will try to light a few times and lock out and you ahve to kull power to the furnace to reset. If this is whats happening clean the sensor nd you should be ok If not you need help from a service tech.Rus
Heat sensor....Or a flame sensor. Flame sensor is connected to a "single" wire under the buners usually found on the left side. Heat sensors (or flame rollout switches) are found surrounding the burner box. The most common bad one will be located just above the burners. it "should" have a small reset button in the middle just between the two wires. If the furnace does light even for a short time the rollout switch is not bad.
I am confident the technician(s) have done this but check anyway.
Gas pressure 4-7 inches W.C for natural, 10 - 11 for Propane.
Air filter clean and unrestricted.
Temperature over supply plenum 140 degrees F.
All registers open and unrestricted.
Vent and intake unrestricted and not blocked.
Condensate hoses free of debris and draining.
OK now lets check to see if the furnace is staying on long enough.When it runs for a heat cycle, is the flame staying on until about 2 minutes prior to achieving the set temperature or is it cycling everyfew seconds and never reaching temp? To check you will need to view the flame through a small viewing port of thru the fins in the front door. Watch them for 10 to 15 minutes.
If they are staying on a long time, we will need to see if the room blower is working properly. If they are going out quickly and or cycling. Get the technician on the pone to talk it over. It could be a safety sensor.
If the blower stays on and the burners are on as well, you have a door open somewhere. Just kidding. Remove the thermostst documenting which wires go where. Take the white wire and cross it with the red wire. This will (or should) turn on the furnace. Clamp them together untill the either the house gets warm or you are confident it is not going to reach temperature. If it did get close to the temperature you wanted, it is a thermostat issue. If not, you got me!
And they say we have an easy job! Get beck to us with your results.
The flame sensor is not sensing flame. Inspect the system as it is tying to start and see if the flames are traveling to all burners and hitting the sensor. If not, clean the burner flame rail (the trough the allows the flame to travel from one burner to the next) or if it is hitting the sensor, clean the sensor with steel wool and check all connections from the sensor to the control board.