Question about Air Conditioners
Run a wire from the sensor down to the control board conector. Bypass the sensor wire around the connector in the blower deck.
The connection can be wire nutted on the sensor lead with the wire (16 or 18 guage stranded wire works) routed through the blower deck to the other side of the plastic wire connector on the blower deck.
The Sensor operates at high voltage but very low current. The connector will sometimes fail due to humidity or wear.
I have seen this on the Rheem or Ruud furnaces.
Hope this helps.
Posted on Jan 07, 2009
Tips for a great answer:
Aug 18, 2014 | Air Conditioners
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 11, 2011 | Air Conditioners
Sep 01, 2010 | Air Conditioners
Jun 11, 2010 | Air Conditioners
Jun 07, 2009 | Air Conditioners
May 30, 2009 | Amana Comfort Zone 12M32PBEH Air...
Jan 16, 2009 | Air Conditioners
Dec 25, 2008 | Air Conditioners
197 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: