Question about Heating & Cooling
Run a wire from the sensor down to the control board conector. Bypass the sensor wire around the connector in the blower deck.
The connection can be wire nutted on the sensor lead with the wire (16 or 18 guage stranded wire works) routed through the blower deck to the other side of the plastic wire connector on the blower deck.
The Sensor operates at high voltage but very low current. The connector will sometimes fail due to humidity or wear.
I have seen this on the Rheem or Ruud furnaces.
Hope this helps.
Posted on Jan 07, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 08, 2013 | Heating & Cooling
Oct 23, 2011 | Heating & Cooling
Sep 22, 2011 | Rheem Tankless Water Heater Main Remote...
Apr 04, 2010 | Heating & Cooling
Dec 12, 2009 | Heating & Cooling
Nov 15, 2009 | Heating & Cooling
Jul 08, 2009 | Water Heaters
Mar 10, 2009 | Goodman GMS90703BXA Heater
198 people viewed this question
Usually answered in minutes!