Question about Air Conditioners
Electric ignition gas pilot works, burners light faintly, but not fully, then die out. Pilot stays lit until I turn off thermostat. Last week, the furnace started acting up-would go through 4-5 cycles of coming on with burners and blower, then blower would go off for a minute or 2, while burners would stay lit. Then blower would come back on after another minute. After several cycles, everything would work. Now the burneres do not fully light, and of course the fan doesn't come on since there is no demand. Fan works fine when I switch it on. I took out the flame sensor to check it and it seems OK. No corrrosion build up, and it glows red hot. Could it be the flame sensor is shot? Furnace is 20 years old.
If the burners do not fully ignite, the sensor will shut the furnace down. The lack of sufficient burner flame is a gas valve or gas pressure problem within the valve.
Replacing the gas valve with the original one may get you going. I surely suggest a professional service company for safety reasons and a thorough inspection. A 20 year old furnace is past it's normal life span.
Posted on Jan 06, 2009
Tips for a great answer:
Oct 08, 2012 | Intertherm Heating Cooling System 15kw...
Mar 11, 2011 | Air Conditioners
Oct 15, 2010 | Air Conditioners
Mar 29, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 28, 2009 | Carrier 38CKC042 Air Conditioner
Nov 16, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 24, 2009 | Coleman Air Conditioners
Jan 16, 2009 | Air Conditioners
Dec 28, 2008 | Ruud UBHC Air Conditioner
Sep 05, 2008 | Air Conditioners
736 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: