Question about Heating & Cooling
Electric ignition gas pilot works, burners light faintly, but not fully, then die out. Pilot stays lit until I turn off thermostat. Last week, the furnace started acting up-would go through 4-5 cycles of coming on with burners and blower, then blower would go off for a minute or 2, while burners would stay lit. Then blower would come back on after another minute. After several cycles, everything would work. Now the burneres do not fully light, and of course the fan doesn't come on since there is no demand. Fan works fine when I switch it on. I took out the flame sensor to check it and it seems OK. No corrrosion build up, and it glows red hot. Could it be the flame sensor is shot? Furnace is 20 years old.
If the burners do not fully ignite, the sensor will shut the furnace down. The lack of sufficient burner flame is a gas valve or gas pressure problem within the valve.
Replacing the gas valve with the original one may get you going. I surely suggest a professional service company for safety reasons and a thorough inspection. A 20 year old furnace is past it's normal life span.
Posted on Jan 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 18, 2015 | Water Water Heaters
Jan 09, 2015 | Heating & Cooling
Apr 05, 2014 | Cozy (W352E) Heater
Nov 19, 2012 | Heating & Cooling
Mar 11, 2011 | Heating & Cooling
Dec 30, 2009 | Heating & Cooling
Nov 16, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 13, 2009 | Heating & Cooling
Sep 16, 2009 | Coleman Propane Forced Air Heater...
Feb 13, 2009 | Imperial Commercial Cooking Equipment...
741 people viewed this question
Usually answered in minutes!