Question about Heating & Cooling
The fan/limit control (silver3x4 box cover pulls off has a dial behind cover with temp graduations) is prob.stuck or out of adjustment.
Posted on Jan 11, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2015 | Heating & Cooling
Nov 16, 2010 | Weather King Heating & Cooling
The pilot light jet may have got a little bit of dirt or grit in it which is preventing it from keeping alight. Try probing the jet with a fine piece of wire to see it the blockage can be dislodged. You may have to unscrew the jet to clear it by blowing air through it. Make sure gas is turned off first before removing any parts.
The pilot light also has a thermocouple that allows gas to the pilot light while the flame is burning. If flame goes out it shuts gas off to the pilot jet. The thermocouple is bypassed by a switch during the initial ignition and once the thermocouple warms up after a minute or two of holding in the bypass switch, it should maintain the pilot. If, after cleaning, the pilot light keeps going out, it would seem that your thermocouple is faulty and needs to be replaced
Sep 27, 2010 | Intertherm Heating & Cooling
Mar 01, 2010 | Desa International GWP20T GLOWARM Wall...
Dec 15, 2009 | Goodman CLQ36AR49 Air Conditioner
May 01, 2009 | 1972 Yamaha XS2
Apr 05, 2009 | Heating & Cooling
Mar 29, 2009 | Desa International GWN10T Wall Mounted...
Jan 06, 2009 | Heating & Cooling
Nov 15, 2007 | Imperial IR-6-C Elite Gas Kitchen Range
50 people viewed this question
Usually answered in minutes!