Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 08, 2015 | Teledyne Laars Laars Lite 2 Pool Heater...
May 11, 2014 | Jandy Lite 2 Natural Gas Pilot Light...
Aug 31, 2013 | Jandy Lite 2 Natural Gas Pilot Light...
Dec 31, 2012 | Reddy Heating & Cooling
it is important to turn off
the gas supply to the water heater at the manual gas shut-off
valve. This valve is typically located beside the water heater.
Note the position of the shut-off valve in the open/on position
then proceed to turn it off.
2. On the lower front of the water heater locate the combination
gas control valve/thermostat. Depress and hold
the lock tab located under the gas control knob on the right.
Rotate the gas control knob on the combination gas control
valve/thermostat clockwise until "OFF" aligns with the mark on
the front of the gas valve. Once the gas supply has been shutoff,
remove outer door. 3. Using a 1/4" nut driver or socket loosen the two screws securing
the manifold door assembly until they are free. Do not
totally remove the screws and plastic retainer washers from
the manifold door. The screws and retainer washers will be
needed to reattach the manifold door. 4. In this step, the thermocouple, manifold tube, pilot tube and
igniter wire will be disconnected from the combination gas
control valve/thermostat. Using a 7/16" wrench
disconnect the thermocouple (left-hand thread) and pilot tube
(right-hand thread). Using a 3/4" wrench disconnect the manifold
tube (right-hand thread). Carefully pull the igniter wire from
the igniter button.
5. Grasp the manifold tube and push down slightly to free the
manifold tube, pilot tube, and thermocouple from the combination
gas control valve/thermostat. when installation is complete and gas is back on, You should be able to relight the pilot and the functionality of your gas hot water heater should be restored.
Nov 27, 2010 | Reliance Natural Gas Water Heater Control
Oct 13, 2010 | Dyna-Glo D-E37 Wall Mounted Panel Heater
Jan 19, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Dec 12, 2009 | Dayton Heating & Cooling
Dec 11, 2009 | Dayton Gas Furnace Heater
Apr 28, 2017 | GE Heating & Cooling
Apr 28, 2017 | Dimplex Heating & Cooling
80 people viewed this question
Usually answered in minutes!