Question about Heating & Cooling
This may be caused by accumulation of sludge in the steam trap (the looped tube that connects the pressuretrol unit to the boiler). the sludge restricts the pressure from reaching the diaphragm in the pressuretrol unit. So it gets a false reading. Clean or replace the tube and see if normal function resumes.
Posted on Dec 07, 2009
Here's a link that may help it explains the controller and how it works. http://customer.honeywell.com/techlit/pdf/PackedLit/60-2341.pdf I personnally would not be adjusting this control as you have been because its a safety that shut off the unit in a unsafe condition. If it's malfunctioning then thaat is when you need to call a service company to check out why. You would not want your unitto explode because of a high pressure condition. Please have your unit serviced.
Posted on Jan 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 21, 2017 | Honeywell Heating & Cooling
on Dec 29, 2009 | Heating & Cooling
Dec 14, 2013 | Honeywell Programmable Thermostat Heater
Aug 07, 2011 | Honeywell Water Heaters
Feb 09, 2011 | Amana PTH123B25AJ Heat Pump Air...
Dec 11, 2010 | Honeywell L4064B2236 Fan/Limit Control...
Dec 29, 2009 | Honeywell Programmable Thermostat Heater
Nov 17, 2009 | Honeywell Programmable Thermostat Heater
Oct 31, 2009 | Honeywell CT87B ROUND HEATING&COOLING...
Jan 13, 2009 | Honeywell Electronic Programmable...
464 people viewed this question
Usually answered in minutes!