Question about Heating & Cooling
Here is my situation:
I have a Goodman (gulp) gaspack Model PGB042125-1 that is approximately 8 years old. In the past we have had to repair the the other regular issues (cracked heat exchanger, multiple bad igniters, burned compressor contacts, etc -- Thanks Goodman!), but I've got a new one and money is tight. The draft induction fan keeps cycling on and off -- regardless of whether the thermostat is calling for heat or not. The gas never turn on during the cycling and the igniter never glows, the induction fan just keeps cycling on and off and has been doing so for weeks. When the thermostat calls for heat, the unit works just fine. Is this a problem with the board that I keep reading about? I'm pretty handy with a volt meter but I have no clue where to start to diagnose the problem and I can't afford to either start replacing parts or pay for a house call to a professional to run the diagnostics. I've searched through the threads and cannot find an example of my problem. Please help me.
Can you write down where the low voltage t stat wire go and disconnect the white wire at the unit to eliminate a short between the white wire and the red wire usually the colors are as follows red is 24volt , green is fan , white is heat, yellow is cooling I want to narrow down the red is not shorting to the white briefly let me know if this is possible if not we can try other checks
Posted on Jan 06, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 27, 2015 | Goodman Heating & Cooling
Dec 17, 2014 | Goodman Manufacturing...
Nov 01, 2013 | Goodman GMS90703BXA Heater
Jan 06, 2013 | Heating & Cooling
Feb 03, 2009 | Heating & Cooling
Nov 18, 2008 | Goodman GMS90703BXA Heater
Oct 02, 2008 | Goodman Heating & Cooling
201 people viewed this question
Usually answered in minutes!