Question about Air Conditioners
First of all, Heat Controller does not mount any schematics on their systems panels at all and supply no information for the service tech to code the light on the outdoor board. This is unbelievable.
Anyway- I found that the electrician had re-arranged breakers in the panel supplying the building and had connected the outdoor heat pump to 120v instead of 240v. He had interpenetrated the connection at the unit that has marked 2(N) as being a neutral connection. I explained that on 120v systems, that is neutral, but on a 240v system, it's L2. The outdoor board was flashing 5 times after the power was turned on for 3 minutes. Voltage at "S" was 38.4v, with this condition and the indoor units lights (all) were flashing every second and beeping as well.
It's running fine now that we are connected to the proper voltage.
Posted on Jan 06, 2009
Tips for a great answer:
Dec 22, 2014 | Fujitsu AOU9RLS HALCYON Mini Split Outdoor...
May 26, 2014 | LG LMN127HVT LMN127HVT 12 000 BTU Ductless...
Oct 18, 2013 | Samsung AQV12VBCN Vivace Mirror Finish...
Jun 28, 2011 | Heat Controller Air Conditioners
Dec 13, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Apr 19, 2010 | Air Conditioners
Feb 01, 2010 | LG LS-K2430HL Heat Cool Mini Split Air...
148 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: