Question about Heating & Cooling
First of all, Heat Controller does not mount any schematics on their systems panels at all and supply no information for the service tech to code the light on the outdoor board. This is unbelievable.
Anyway- I found that the electrician had re-arranged breakers in the panel supplying the building and had connected the outdoor heat pump to 120v instead of 240v. He had interpenetrated the connection at the unit that has marked 2(N) as being a neutral connection. I explained that on 120v systems, that is neutral, but on a 240v system, it's L2. The outdoor board was flashing 5 times after the power was turned on for 3 minutes. Voltage at "S" was 38.4v, with this condition and the indoor units lights (all) were flashing every second and beeping as well.
It's running fine now that we are connected to the proper voltage.
Posted on Jan 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 22, 2014 | Fujitsu AOU9RLS HALCYON Mini Split Outdoor...
Jul 07, 2008 | Frigidaire Dishwashers
Feb 14, 2008 | Kitchen Ranges
Oct 18, 2013 | Samsung AQV12VBCN Vivace Mirror Finish...
Nov 17, 2010 | Kenmore Dryers
Apr 19, 2010 | Heating & Cooling
Nov 11, 2009 | Whirlpool Duet 7.0 Cu. Ft. Super Capacity...
Jul 19, 2009 | Frigidaire FEF365AS Electric Kitchen Range
Apr 23, 2008 | Refrigerators
148 people viewed this question
Usually answered in minutes!