Question about Heating & Cooling
Look at the coils they look ok and the fuse box looks alright to the main breaker box gets real hot when the furnace is on for about 15 min then blows the fuse replaced the two 60 amp fuses and also the main 200 amp but still goes out some one said they might have put the wire to the furnace backwards but it the same problem as before wondering if the little dieod that in the mid of the unit on the blow box might be bad the one on the top looks alright but the one on the bottom looks lik it has some stuff on it and if theres a tool or meter that has a surge reader on it to tell me what breaker it is
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 18, 2015 | Heating & Cooling
Nov 18, 2013 | Goodman Heating & Cooling
Dec 28, 2010 | Carrier 38CKC036 Air Conditioner
May 24, 2010 | Heating & Cooling
Apr 11, 2010 | Goodman CLJ36AR42 Air Conditioner
Aug 17, 2009 | Dometic Rooftop RV Air Conditioner
Jan 16, 2009 | Heating & Cooling
Dec 22, 2008 | Intertherm P3RA-048K Air Conditioner
Mar 14, 2008 | Dometic Rooftop RV Air Conditioner
Sep 03, 2007 | Heating & Cooling
Jan 24, 2017 | DeLonghi Heating & Cooling
87 people viewed this question
Usually answered in minutes!