Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
having a problem with a weather maker 8000. It will not come on at all unless I shut down the switch on the side of the furnace. filters is clean. it will start to light then stop
Posted on Dec 20, 2008
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Nov 28, 2009
Tips for a great answer:
Nov 21, 2015 | Heating & Cooling
on Jan 08, 2015 | Heating & Cooling
Apr 13, 2014 | Carrier Furnace Control Board Bryant...
Dec 21, 2012 | Heating & Cooling
Feb 12, 2012 | Heating & Cooling
Sep 21, 2011 | Coleman Heating & Cooling
Dec 23, 2010 | Carrier Heating & Cooling
Nov 30, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 23, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 11, 2009 | Heating & Cooling
26 people viewed this question
Usually answered in minutes!