Question about Dayton Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If you intend to use this in a residential garage, you will have to use standard galvanized round pipe coming off the unit, 24 gauge will suffice, use a minimum of 6”-8” from the unit. From there you will have to make the transition to the B-Vent. Always double check with you local codes in your area.
Hope this helps.
Posted on Dec 02, 2008
you can look for a gas that we go in place of the one you have, try national energy they sell gas valves and should have one to fit your heater , i would change the thermocouple as well .
hope this helps
Posted on Dec 08, 2008
not hard but before replacing check pilot light and thermocouple for proper function and setting if pilot light not in right position thermocouple wont open gas valve if electronic ignition check for power and proper gap on igniter also check stat for proper function
Posted on Oct 31, 2009
Tips for a great answer:
Mar 22, 2017 | Dayton Heating & Cooling
Oct 31, 2015 | Dayton Heating & Cooling
Sep 15, 2011 | Dayton Gas Furnace Heater
Jun 08, 2011 | Dayton Gas Furnace Heater
Oct 31, 2009 | Dayton Gas Furnace Heater
Oct 02, 2009 | Dayton Gas Furnace Heater
Jan 07, 2009 | Dayton Gas Furnace Heater
Dec 08, 2008 | Dayton 511 Utility Heater
166 people viewed this question
Usually answered in minutes!