Question about Siemens Seimens Arc Fault Breaker
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The white coiled wire should be connected to the neutral bar with all the other white wires. The neutral from the circuit it controls should then be connected to the breaker. If you're reading your meter between the hot conductor (black wire) and the neutral (white wire) that would be normal. If you remove the wire from your neutral bar to test it, and you have a load on the circuit you will be reading voltage out through your load and back on the neutral and it would "appear" to be hot. But why would you remove the white wire? What is the original problem, is the breaker triping?
Posted on Jul 01, 2010
Tips for a great answer:
May 27, 2015 | Electrical Supplies
Aug 05, 2013 | General Electric G.E. - INDUSTRIAL SYSTEMS...
Jul 13, 2012 | Square D Co. QO220 Circuit Breaker
Apr 26, 2012 | Siemens /ite Bq Circuit Breaker Bq3b090 3p...
Feb 27, 2012 | General Electric GE 125 Amp Indoor Main...
Jun 18, 2011 | Square D Co. QO612L100S Main Lug Load...
May 18, 2010 | Siemens Seimens Arc Fault Breaker
Jun 28, 2009 | General Electric G.E. - INDUSTRIAL SYSTEMS...
Feb 09, 2009 | Square D Ehb24020pl 20 A Ehb4 Ehb Circuit...
Aug 01, 2017 | Siemens Seimens Arc Fault Breaker
63 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: